PT900 check meter
In Northern China there are many water plants with lots of large electromagnetic flow meters. Per local regulation these need to be verified once a year. The verification is a cumbersome process, takes a lot time and money for the water plants.
A plant operator needed a check meter that could install easily, without interrupting the flow, to assess the installed electromagnetic meter. The verification should obtain a measurement error between the two meters that stays within an acceptable ±2% error limit, then inline meter verification cycle can be extended to 2 years or more.
The following features were required from the check meter: 1. Accuracy within ±1% of reading 2. Online data storage for a month 3. 2 channels
The Panametrics Transport PT900 clamp on flow meter was used with C-RS 401 transducer to verify a DN800 (32”) Mag meter for a three-month period. The average difference between the meters were below 1.5%.
The customer was satisfied with Transport PT900 performance and ordered two additional units. The customer managed to reduce their maintenance budget while increased the plant availability and yield.
Learn more about Panametrics Portable Flow Meters
Download the Application Note here
Join the conversation on LinkedIn